The Lew Electric FBKIT is a round PVC floor box with (2) 3/4″ hubs, (2) 1″ hubs, (2) 3/4″ reducers, (4) 1/2″ reducers. It features a slot to make the box divided for power and data, not included but can be purchased as part number FBDIV. The outside diameter is 5", and the inside diameter is 4.5". The LRA-U adapter ring is included so you can install any 32 series cover. Please see installation instructions below:
1.Set floor box on level surface or secure to form with screws at the four pre-molded corner holes.
2.Solvent cement conduit into corresponding holes in box.
3.Pull wiring through into the floor box.
4.Attach concrete cover and seal vacant holes with cemented plugs provided.
5.Pour concrete to desired depth.
6.Remove and discard concrete cover. Use a hand saw to cut box above the set concrete.
7.Attach cover assembly (see approved covers below) to included leveling ring (part # LRA-U) using screws provided with that cover. Affix wiring in the box to the device (not provided.)
8.PVC glue the exterior of the leveling ring and place cover and leveling ring assembly inside floor box and set in place.
9.If this box is used for low voltage and line voltage, a partition must be used (part # FBDIV.) Prior to installing partition, take inside measurement from bottom to top of box. Deduct the measurement of the box against the height of the partition and allow an extra 1/8” for slight variation and proper fit to the leveling ring. Mark this length on the partition measuring from top to bottom and make a horizontal cut across partition. This cut should always be towards the bottom of the partition, and not the top (narrower side.) Partition is notched at the top to fit along inside groove of leveling ring. Drop partition in the slotted channel of the floor box. Note that when covers are used for both line and low voltage simultaneously, the low voltage connections are made loose in the box (connection will be made underneath the cover)and are on the side of the partition with the least amount of cubic inch capacity.
10.Approved covers for use with LEW part # LRA include: DCF-1-X-GFI, PFC series, and TCP series covers. Visit our website at www.lewelectric.com for more information.
11.Our covers along with the LRA-U will fit into a Carlon or Krayloy brand round PVC box as well.
1 year warranty
Use in concrete floors only
5" outside diameter
4.5" inside diameter
Use with 32 series covers
(2) 1″ hubs
(2) 3/4″ reducers
(4) 1/2″ reducers
Adapter ring included
UL listing #514C
1 year warranty
Questions & Answers
Have a Question?
Be the first to ask a question about this.